CAN ULC S536 PDF
CAN/ULC-S PERIODIC INSPECTIONS AND TEST – DAILY AND MONTHLY. NOTE: Refer to Appendix D for examples of Inspection and Test Record. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected. 1 SCOPE This Standard prescribes requirements for the inspection and testing of fire alarm systems and specifies the devices and functions.
|Published (Last):||19 July 2016|
|PDF File Size:||2.84 Mb|
|ePub File Size:||15.5 Mb|
|Price:||Free* [*Free Regsitration Required]|
Post indicator valves opened until spring or torsion is felt in rod. Plug-in cables securely in place. Please review additional Ccan 9 testing requirements on the Passive Systems page.
Displays are visible in the installed location.
Recommended Additional Visual Inspection not mandated by the Standard: When sufficient particles accumulate, the unit goes into an alarm condition. Door holders and releases you, as the building owner, should know the difference and how they operate on a fire alarm activation ; Elevator recall functions general alarm homing, alternate floor homing, and machine room and shaft fire operation ; Smoke control functions electrically operated dampers, fans, pressurization fans, etc.
H Operation of voice paging does not interfere with initial inhibit time of alert I signal and alarm signal. Annual Tests Control valves shall be operated through its full range and returned to normal. Individual alarm and supervisory input zone designation labels are properly identified. AA Fire alarm reset function operates.
CAN/ULC-S | Standards Council of Canada – Conseil canadien des normes
Minor leak at no flow? Each power loss i. Fire hose connection undamaged?
Supporting field devices must also be listed. Refer to Appendix Ullc ; P iii Silent accelerated test. If in doubt, replace the unit and dispose of the old one in a safe manner. These sensors have a limited service ss536 usually ten years and some require regular battery replacement. Steam from your hot bath, shower, or operating dishwasher may accidentally “set-off” one of these units.
The attached reports comply with Canadian Inspection Standards upon which they are based. Valve handles in place?
Microphone, including press to talk switch, operates. Backflow prevention assemblies have been tested by an agency acceptable to the local authority?
Spare sprinklers shall be inspected? Magnetic door holder release activated by fire alarm system? Low points in dry systems drained prior to freezing weather?
Standards Council of Canada
Hose Rack Pressure Reducing Valves: Sensitivity tested results are recorded in the Device Test Record. Smoke particles obscure the receiver, and the unit goes into alarm. Proper light function – power loss? G Confirm that the supervisory transmission to the fire signal receiving centre is received.
Fuel levels and a low fuel trouble indication the low fuel alarm set point should be checked to ensure the unit is cn to deliver emergency power for the duration required by the Building Code for the type of occupancy; In-suite signals if equipped with a silence feature must be checked for proper operation of the silence function including resounding if signals are silenced and a second alarm zone is activated ; Duct mounted smoke detectors must be individually tested and some rather detailed results recorded namely the differential pressure and the sensitivity reading on the Individual Device Test Record ; Stand-alone capabilities of networked systems must be tested and properly documented; Sprinkler system interconnection isolation valve supervisory signals, flow switch alarm, tamper, low temperature, heat trace controller trouble and supervisory, low air, etc.
Diesel tanks and overflow piping unobstructed? Building diagrams are on site that clearly indicate the type and location of all smoke control equipment fans, dampers, etc. Ss536 the building fully sprinklered? Annual Operate emergency starting means without power Trip circuit breaker if provided? Testing results and any exceptions are identified in the Device Test Record.
Yes No Last Service Date: Description of the area or fire zone protected by each alarm detection circuit dan may be in the form of a list or plan drawing. Yes No Time for motor to accelerate to full speed: Manual transfer from alert signal to alarm signal.
Operation of the fire signal receiving centre transmitter bypass means results in a specific I trouble indication at the fire alarm control unit or transponder Operation of the fire signal receiving centre disconnect means transmits a trouble signal to J the fire signal receiving centre. Visual indicator test lamp test operates. Common uc trouble signal operates. Hand wheel is not broken or missing?
CAN/ULC-S536-04 Fire Alarm Annual Inspection Test Form
Smoke and fire detectors should be considered an integral part of any home or business security system. The fire signal receiving centre is ULC Listed. Applying household voltage to the interconnection wire will result in the destruction of any connected alarms and may even cause a fire.
Inspect air pressure and water pressure? Visual trouble signal operates. Will racks swing out of the cabinet at least ninety 90 degrees? Output circuit designations correctly identified in relation ylc connected field devices.